- Building Approvals
- Combustible Cladding
- Inspections & Certificates
- Forms & Fact Sheets
- Contact Us
Clause 126.96.36.199(a)(i) of the Building Code of Australia (Volume 2) requires smoke alarms to be installed between each part of the dwelling containing bedrooms and the remainder of the dwelling.
Following complaints from smoke alarm inspectors, the QBCC has taken a literal interpretation of the BCA, and therefore where floor plans have bedrooms which open onto another room such as a TV room or family room, a smoke alarm must be located outside of each bedroom door. This will mean that in many cases, additional smoke alarms may need to be installed than was previously allowed.
The previous practice of building certifiers was a pragmatic one, whereby smoke alarms were required in locations where occupants would be adequately alerted ie in proximity to bedroom doors rather than in front of each door.
The HIA is discussing this matter with the State Government. In the meantime, building certifiers are required to comply with the direction of the QBCC.
Brisbane City Council has recently proposed a citywide amendment to restrict townhouses from single-home areas. Townhouses are an affordable housing solution that provides diversity…
Substantial increase in relaxation fees – Brisbane City Council The Council has significantly increased their fees: Express – $218.45 to $590 Fast Track –…
The Gold Coast City Council has changed their standard driveway drawings to provide more flexibility. The middle section W2 can now be up to 5m…